15 - 20 June
The control unit has been made up of modules, which make it easy to expand and service it. The basic version is equipped with power supply, control system, display and loop module. Expanding the control and adjusting it to your own needs can be done by installing and programming corresponding expansion cards.The control units are produced and sold in a couple of casings. The casing may or may not be equipped with a log printer (installed on the front door).Maximum 4 expansion cards (e.g. a line module) can be connected to the fire alarm control unit. The unit consists of a control panel made up of LED indicators, some buttons, as well as 7-inch high resolution display. In the event of a system failure the basic system automatically switches to the backup system (redundancy) which carries on with all the functions asper EN 54-2 norm.The display is available in several language versions.The event log memory has the ability to store minimum 50,000 events. The memory and configuration can be stored on SD card. All saved events can viewed on a control panel and printed out by means of an inbuilt printer or viewed by means of the service tools and then printed from a PC. If more sensors need to be monitored, the system can be expanded by adding more interacting control units.Fire alarm control units can be interconnected by means of the so called networking. The ESP remote control panel can also be connected to communication line in order to control each unit as well as to configure individual systems.Networking the control units allow for designing the large, decentralized fire alarm systemsused in any type and any size of buildings.Optionally, the control units can be monitored via TCP/IP protocole. Remote access to the system can be obtained by means of a PC via dedicated software.
The TS detector is normally equipped with two detectors: the detector of temperature and smoke. The application of two sensors allows for swift and reliable detection ...
Our TSC detector is normally equipped with three sensors detecting temperature, smoke and carbon monoxide. The application of three sensors allows for quick and ...
This ROP-21 manual call point is used to transfer information about fire alarm to a control unit by a person who noticed fire and who manually activated the call ...